and WATFORD, England,
March 29, 2013
/PRNewswire/ -- The following is a notification from UL and the Loss Prevention Certification Board (LPCB) to distributors, contractors, fire departments, regulatory agencies, and authorities having jurisdiction that the Fire Sprinkler identified below bears a counterfeit UL Certification Mark for
the United States
, and a counterfeit LPCB Mark. The Fire Sprinkler has not been evaluated by UL or LPCB to the appropriate Standards for Safety and it is unknown if the Fire Sprinkler complies with any safety requirements.
Although the fire sprinkler wrench boss is marked "TYCO" and the thermo bulb is marked "JOB F5" the fire sprinkler was not manufactured by Tyco International, Inc., and the thermo bulb was not manufactured by Job, GmbH.
Note that the counterfeit fire sprinkler is constructed similar to a fire sprinkler that is authorized to bear the UL and LPCB Marks. The counterfeit sprinkler is marked "2012" on the wrench boss of the fire sprinkler frame. The fire sprinkler that is authorized to bear the UL and LPCB Marks is not marked "2012" on the wrench boss of the fire sprinkler frame.
Name of Product:
Horizontal sidewall fire sprinkler.
On the product:
The product bears counterfeit UL and LPC Marks and the following information on the sprinkler deflector: "155ºF/ 68ºC" and the wrench boss is marked "TYCO" and "2012".
UL is a premier global independent safety science company with more than 118 years of history. Employing more than 10,000 professionals with customers in over 100 countries, UL has five distinct business units – Product Safety, Environment, Life & Health, Knowledge Services, and Verification Services – to meet the expanding needs of our customers and to deliver on our public safety mission. For more information on UL's family of companies and network of 95 laboratory, testing, and certification facilities, go to UL.com.