This account is pending registration confirmation. Please click on the link within the confirmation email previously sent you to complete registration. Need a new registration confirmation email? Click here
Feb. 22 /PRNewswire/ - ATI AirTest Technologies (TSXV:AAT) announced today that its proprietary carbon monoxide (CO) sensor-based garage ventilation system achieved a 93.9% kilowatt hour (kWh) savings and 95.7% reduction in peak kilowatt (kW) demand at a 220-car parking garage in the heart of
San Francisco's financial district. Engineers for the regional utility, Pacific Gas & Electric (PG&E), verified the savings.
Nagle Energy Solutions (NES), a leading green-technology consulting, sales and installation company, sold, designed and installed the system at 600 California Street, which is owned and operated by
Boston-based Beacon Capital Partners.
"The combination of AirTest's innovative technology and Nagle Energy Solutions' ventilation strategy and project design, including accurate power-consumption measurements and detailed calculation methodologies, is exceptional," said
Alfred Scaramelli, Senior Vice President for Beacon Capital Partners. "They delivered exceptional energy savings."
The CO sensor-based, demand control ventilation (DCV) system utilizes a proprietary, smart-control logic that detects and measures vehicle fumes in the garage space and then modulates fan speeds to prevent CO levels from exceeding 10 parts per million (ppm) for extended periods of time. This enables it to consistently achieve greater energy savings - up to 95% - than traditional "on/off" sensor based ventilation control systems while better ensuring the health and safety of building occupants and visitors by providing continuous ventilation.
The 600 California Street garage is ventilated by five (5) exhaust fans totaling 130 horsepower (HP). Combined, the garage fans consumed 241,655-kilowatt hours (kWh) and 91.62 peak kilowatts (kW) per year at an annual cost of
$25,100. Post-installation data logging by PG&E engineers showed AirTest's smart-control logic and the NES ventilation design achieved an annual energy savings amounting to 226,899 kWh and 87.7 kW in demand reduction. That represents a 93.9% reduction in kWh consumption and a 95.7% decrease in peak kW demand when operated on the recommended time schedule. According to
George Graham, President of AirTest, "These types of savings are typical of what we can achieve with the AirTest approach to garage ventilation control".
Upon verifying the energy savings, PG&E issued a
$21,500 rebate to 600 California Street property management. The garage DCV system will pay for itself in just 22 months, and Beacon Capital Partners' annual cost(s) to ventilate its garage will drop by
$23,600 - a 94% decrease.
About AirTest: AirTest Technologies, Inc. (
www.airtest.com) is a Green-Tech company specializing in sensors that improve commercial building operating efficiency and, at the same time, generate energy savings. These sensors are all based on technical innovations developed in the last 10-plus years and comprise a growing second wave of energy saving technologies that make a significant contribution to the sustainability of buildings. AirTest offers its products to leading-edge building owners, contractors and energy service companies targeting the buildings market.
About NES: Based in
Menlo Park, CA, Nagle Energy Solutions (
www.nagle-energy.com) is a green technology consulting, distribution and installation company providing expert strategies and superior technologies designed to dramatically improve commercial and governmental property operating efficiencies and, as a result, generate sizable energy savings. In particular, NES sells/installs AirTest's carbon monoxide (CO) and carbon dioxide (CO2) sensor systems, each of which significantly reduce energy costs. NES extends its sales, service and installation capabilities to all major U.S. markets.
Statements about the Company's future expectations and all other statements in this press release other than historical facts are "forward looking statements". The Company intends that such forward-looking statements be subject to the safe harbours created thereby. Since these statements involve risks and uncertainties and are subject to change at any time, the Company's actual results may differ materially from the expected results.
SOURCE AirTest Technologies Inc.